NYU Hospital’s Backup System Undone by Key Part in Flooded Basement
official explains how move to rooftop generators failed to prevent failure of
backup power during Hurricane Sandy
After Hurricane Irene, officials at NYU Langone Medical Center spent several million dollars protecting its backup power system from flooding, according to Richard Cohen, vice president of facilities operations.
The hospital removed a fuel tank and a set of emergency generators at street level and chose to depend on what Cohen termed an “extremely modern, extremely reliable” system of rooftop generators.
The hospital also built a new, flood-resistant house for pumps that draw fuel from the hospital’s sealed underground tank and feed it to the generators that make electricity when New York City’s power fails.
One vulnerability remained, and it proved to be the system’s Achilles Heel. A portion of the hospital’s power distribution circuits, which direct the generated electricity out into various areas of the hospital, were located in the hospital’s basement.
“It’s like what happens when you have a flood in your basement and the electrical panel is in your basement,” Cohen said.
The predicted storm surge heights feet from Sandy did not worry NYU officials. “We had Hurricane Irene last year,” Cohen said. “We did not have any compromised or flooded areas in the hospital, so frankly we had no reason to think this would be any specific risk.”
However, the National Weather Service upgraded its predicted storm surge heights for lower Manhattan to as high as 11 feet as early as Sunday morning. That day, dozens of EMS units could be seen idling in front of NYU Langone Medical Center. EMTs said they were standing by to transfer patients. But the hospital leadership decided to keep the patients in place.
NYU’s Cohen stressed that the hospital’s system complied with building codes at the time it was constructed. Hospitals are generally not required to upgrade their systems to current code.
Even newly built hospitals in low-lying coastal zones are not necessary required to flood-proof their systems, according to George Mills, director of the engineering department at the Joint Commission, the organization that accredits most American hospitals.
Mills said his organization and the U.S. Centers for Medicare and Medicaid Services require hospitals to adhere to the 2000 edition of National Fire Protection Association life safety code. It calls for “careful consideration” to be given to protecting electrical components from “natural forces common to the area” such as storms, floods and earthquakes.
The 2012 version of the code upgrades that language, saying the systems “shall be designed” to protect against these hazards. However, CMS and the hospital accreditation agency have not yet adopted this edition.
“All of these systems are only as reliable as the weakest link,” Mills said.
During the storm, according to Cohen, the hospital also experienced a temporary loss of the system that pumps fuel to the generators. That occurred when a rapid, forceful rise in water breached the underground vault that holds the fuel tank. Sensors within the vault automatically shut off the fuel pumps.
“As soon as the staff was able to access that pump house, able to reset the pumps, they were able to feed fuel to those generators and those generators are running now.” Cohen estimated the loss lasted about an hour. During that period, he said, hospital leaders decided to evacuate.
After the pumps came back online, he said, areas of the hospital where backup power is distributed through a circuit panel located on a higher floor of the hospital regained electricity, including the intensive care units and labor and delivery.
Cohen said the hospital’s elevators were also powered through the upper level circuits and had safety features to keep them from running into the floodwater that had poured into their shafts. The hospital decided not to use the elevators out of concern for safety. “There would have been a very good chance the elevators would have failed,” Cohen said. “We then would have had an elevator extraction in the middle of patient evacuation and that was a prospect that really nobody wanted to face.”
Cohen said the hospital is in the midst of constructing its own power cogeneration facility. When that is completed, the basement-level distribution circuits that proved the system’s downfall during Sandy will be relocated to an upper level. “We’ve purchased all the equipment,” Cohen said. “We currently expect to have it completed sometime around 2014.”
More than 1 million patients suffer harm each year while being treated in the U.S. health care system. Even more receive substandard care or costly overtreatment.
The Story So Far
Too many patients suffer harm instead of healing in U.S. medicine. That’s why ProPublica’s reporters have investigated everything from deadly dialysis centers and dangerous hospitals to the failure of state boards to discipline incompetent nurses.
This page allows patients, providers and readers to join the patient safety conversation. Our goal is to find out why so many patients are suffering harm and highlight the best ways to solve the problem. Here you’ll find regular updates, and places to share your stories, views or expertise.
Read all of our posts on patient safety, and find out how to get involved.
Got a tip? Fill out our form.
Share Your Story
Your input can help ProPublica's reporting.
Have you worked in health care? Tell us what you’ve observed about patient safety.
Have you or a loved one been harmed? Tell us about it.
Join the Discussion
Join the over 1,500 members of ProPublica's Patient Harm Group to learn, share your story and connect with others.
Icon graphics courtesy of the Noun Project.
Latest Stories in this Project
Our Hottest Stories
- In Desegregation Case, Judge Blasts School Officials and Justice Department
- Meet the Online Tracking Device That is Virtually Impossible to Block
- California Halts Injection of Fracking Waste, Warning it May Be Contaminating Aquifers
- What We Learned Investigating Unpaid Internships
- Who Advised Cuomo on Mortgage Industry Investigation? A Mortgage Lobbyist
- Thank You for Your Service: How One Company Sues Soldiers Worldwide
- Are Patient Privacy Laws Being Misused to Protect Medical Centers?
- New York State of Fracking: A ProPublica Explainer
- Error: You Have No Payments from Pharma
- Even After Open Enrollment, Activity Remains Unexpectedly High on Federal Health Insurance Exchange